for Odenton, MD
First Class Employee
ANWAY - Odenton, MD
Couldn't have had a better Experience! Darrell is smart, courteous, and knowledgeable. He is a keeper who makes your company look good to the consumer.
Friendly and professional
Tamara - Odenton, MD
Got the job done with a friendly attitude
GRANGER - Odenton, MD
I've used My Plumber Heating and Cooling for a few years now. I've never been disappointed with the overall service and the technicians working to repair the problem. I would like to thank technician Stephanie High for completing all repairs and answering any questions or concerns during the repair process.
CHARLES - Odenton, MD
DAVIS - Odenton, MD
My rep was very nice, informative and wore booties in my house. Great job and I would use them again!
Replaced blower wheel with original unit. Changed humidifier water panel and verified water solenoid operation, ensured proper drainage. Reset water panel indicator and set humidistat at 35%, winter mode.
install w/c tank
Upon arriving spoke to tenant and found that the system is leaking water onto the floor in the hallway. Customer advised that homeowners association had someone come out and they told him that the unit was leaking water but did not inspect the system. Advised customer that the drain line is clogged as water is filled to the top of the drain pan. Quoted homeowner price for repair and he agreed with that price. Cleared drain line and P-trap using brush and compressed air. Drain is now draining properly at this time. Used credit card homeowner provided with the call for payment of services per homeowners approval.
W/C - 2ND BATH - LEAKING
Checked system and found to be slightly low on refrigerant due to a leaking valve stem. When I removed the Valve cap It was covered in oil and instantly started leaking slightly as I removed it. Replaced valve stem and add it to 2.4 pounds of R410 refrigerant. Installed ceiling valve caps on valves. Test the system and system is operational and cooling properly at this time.
Old toilet removed new toilet put together and ready
replace 2 valves under kitchen sink