for Burke, VA
Fantastic commuicator from the representative.....
ROBERTS - Burke, VA
Lee was wonderful and every so polite. The only negative was the price for the replacement parts..... Believe he really cared about us. We liked him very much.
Good experience. Very satisfied
Mary - Burke, VA
AC conked out. They responded quickly and fixed it. Apparently a fuse had blown on the exterior unit.
SINGH - Burke, VA
Outstanding service, put me at ease he could fix same day
MARIELLO - Burke, VA
Margaret - Burke, VA
Replaced the motor, fan electrical absorption system, and installed a hard start system.
Located bad capacitor at outdoor unit Replaced capacitor and checked ops System is low on refrigerant Went over options with customer Recommended system upgrade due to age, cost of repairs, and efficiency.
Installed new 3/4" PRV and 3/4" shutoff valve with two years parts and labor warranty.
Came out today and cleaned condenser coil with condenser coil cleaner. We installed the and recommended re-evaluating the system. System evacuation is $1200.00 will discount it down to $960.00. However system is cooling at this time
CHECKED SYSTEM AND FOUND A BAD DUAL VOLTAGE ABSORPTION SYSTEM IN CONDENSER UNIT, REPLACED WITH NEW AND TESTED SYSTEM GOOD.
Replaced flow control valve
Installed new quarter turn ball valve for the front hose bib
Arrrived to find evidence of sewer backing up in basement. Snaked line 50 feet and hit blockage, then ran another 12 feet to be safe. Ran water for 10 minutes and everything is draining at this time. Snaked through basement cleanout